|How often do I need to change my air filter?|
|There are many factors that can determine when an air filter should be changed. How often the HVAC unit runs, air quality, humidity and other factors can vary greatly from application to application. For most 1”, 2” and 4” deep panel or pleated style filters, it is usually recommended to change the filter every 2-3 months. In many commercial and industrial applications static pressure can be monitored and the filters can be changed when they reach their recommended final resistance in inches of water gauge.|
|What is MERV?|
|MERV means Minimum Efficiency Reporting Value which was developed by the American Society of Heating, Refrigeration and Air Conditioner Engineers – ASHRAE. MERV values vary from 1 to 16. The higher the MERV value is the value the more efficient the filter will be in trapping airborne particles.|
Understanding MERV (National Air Filtration Association – NAFA)
Filter MERV Descriptions.
|MERV Std 52.2||Intended Dust
Std 52.1 (2)
|1-4||<20%||60 to 80%||> 10.0 μm||Residential/Minimum
Minimum Equipment Protection
Washable/Metal Foam/ Synthetics
Fiberglass / Synthetics
|5-8||<20 to 60%||80 to 95%||3.0-10.0 μm||Industrial Workplaces
Better / Residential
Paint Booth / Finishing
Extended Surface Filters
Media Panel Filters
|9-12||40 to 85%||>90 to 98%||1.0-3.0 μm||Superior/Residential
Better Commercial Buildings
Rigid Cell / Cartridge
|13-16||70-98%||>95 to 99%||0.30-1.0 μm||Smoke Removal
Hospitals & Health Care
Superior / Commercial Buildings
|Rigid Cell / Cartridge
Rigid Box / Son-Supported /
|MERV Std 52.2||Efficiency||Typical Applications||Typical Filter Type|
|17-20 (1)||99.97%-99.9999%||Hospital Surgery Suites
Note: This table is intended to be a general guide to filter use and does not address specific applications or individual filter performance in a given application. Refer to manufacturer test results for additional information.
(1) ASHRAE does not have a test procedure for HEPA testing and has thus dropped the MERV 17-20 classifications.
(2) ANSI/ASHRAE 52.1 ranges are provided for reference only. The ANSI/ASHRAE 52.1 Standard was discontinued as of January 2009.
#2 - 1455 Brigantine Drive. Coquitlam BC, Canada. V3K 7C2 Toll Free: 877-946-7686 Local : 604 525-6100 Local Fax : 604 525-6111